Lightweight Classic Universal Phase Clamps (CCRU, CCNU and CCTU type) can be applied on a wide variety of conductor bars of rectangular or cylindrical section and on spherical pieces (ball studs) of 20 / 25 mm diameter.
There are two clamp sizes: the Lightweight Classic Universal Reduced Clamp (CCRU), Lightweight Classic Universal Normal Clamp (CCNU) and the Lightweight Classic Universal Transversal Clamp (CCTU). The clamps are applied on the conductor by attaching / hanging on the conductor bar / piece.
Both are screw-fastening clamps, allowing the tightening of conductor bar or piece between the clamp’s body and the mobile jaw. The tightening force is provided by the clamping torque of the clamp’s driving screw. Both the clamp body and the jaw are aluminium alloy die cast items. The clamp’s driving screw has usually a “RO bayonet”: CCRU/E, CCNU/E or CCTU/E end but other ends are available: “hexagon 12”, “DIN bayonet”: CCRU/C, CCNU/C or CCTU/C, insulated handle: CCRU/B, CCNU/B or CCTU/B or slidingcross rod: CCRU/p, CCNU/p or CCTU/p. Having small dimensions and lightweight construction, these clamps are recommended for use in low voltage power installations and in other power installations where the spaces between the conductor bars are extremely small or where the application of the clamp is made from a small distance.
The dismounting of the clamp from the conductor is similar for all types of screw-fastening clamps, more exactly the driving screw is unscrewed, the mobile jaw is lowered until there is sufficient space to detach the clamp from the conductor bar / piece.
|Clamp type||LIGHTWEIGHT CLASSIC UNIVERSAL REDUCED CLAMP (CCRU)||LIGHTWEIGHT CLASSIC UNIVERSAL NORMAL CLAMP (CCNU)||LIGHTWEIGHT CLASSIC UNIVERSAL TRANSVERSAL CLAMP (CCTU)|
|Code||P 2402-0-00||P 2403-0-00||P 2449-0-00|
|Nominal short-circuit for t = 1 s Isc (kA)||12,5 kA/1s||23,75 kA/1s||30 kA/1s|
|Clamp body execution procedure||Cast body||Cast body||Cast body|
|Material||Aluminium alloy||Aluminium alloy||Aluminium alloy|
|Diameter of the conductor where the phase clamp can be applied (mm)||Ø 4÷30||Ø 4÷36||Ø 3÷45|
|Diameter of the sphere (mm)||Ø 20 / Ø 25||Ø 20 / Ø 25||Ø 25|
|Thickness of conductor bar where the phase clamp can be applied||30||45||45|